Production of 35 electrical panels for Continental AR, the 6 MDBs of them being the most important.
Assembly, mounting, testing and commissioning for 6 x MDBs:
- Prisma P and Schneider switchgears
- Feeders; 2500 kVA electrical transformer
- Copper busbar system 4000 A and 65 kA, TN-C input, TN-C outputs
- The outputs are on circuit breakers type MTZ1; 3200 A and NS 1250 A
- The inputs are monitored with METSEPM 5560 which is a 2-output Power Meter for energy cost and basic network management
- The outputs are counted with devices type METSEPM 2220 and the circuit breakers status are monitored in BMS